Power monitor apparatus and method with object oriented structure

ABSTRACT

An object oriented architecture is used within individual monitoring units. The monitoring devices include circuitry which receives an electrical signal and generates at least one digital signal representing the electrical signal. Objects within such individual monitoring units include modules which perform a function and registers which contain the inputs, outputs and setup information for the modules. Methods can be invoked on all objects to change or query the operation or configuration of the device. At least one of the modules receives the digital signal as an input and uses the signal to generate measured parameters. Additional modules take measured parameters as input and generate additional parameters therefrom. The module may be linked in an arbitrary manner to form arbitrary functional blocks.

This application is related to U.S. patent application Ser. No. 08/367,534 filed concurrently with this application and entitled "High Accuracy Power Monitor and Method".

MICROFICHE APPENDICES

Included is microfiche Appendix A including three sheet having 282 total frames and microfiche Appendix B including one sheet having 20 total frames.

A portion of the disclosure of this patent document contains material which is subject to copyright protection. The copyright owner has no objection to the facsimile reproduction by any one of the patent disclosure, as it appears in the Patent and Trademark Office patent files or records, but otherwise reserves all copyright rights whatsoever.

BACKGROUND OF THE INVENTION

The present invention relates generally to digital power monitoring. More specifically, the invention relates to a digital power monitoring system using an object oriented structure. The present invention also generally relates to an improved object oriented structure.

Monitoring of electrical power, particularly the measuring and calculating of electrical parameters, provides valuable information for power utilities and their customers. Monitoring of electrical power is important to ensure that the electrical power is effectively and efficiently generated, distributed and utilized. As described in more detail below, knowledge about power parameters such as volts, amps, watts, phase relationship between waveforms, KWH, KVAR, KVARH, KVA, KVAH, power factor, frequency, etc. is of foremost concern for utilities and industrial power users.

Typically, electricity from a utility is fed from a primary substation over a distribution cable to several local substations. At the substations, the supply is transformed by distribution transformers from a relatively high voltage on the distributor cable to the lower voltage at which it is supplied to the end consumer. From the substations, the power is provided to industrial users over a distributed power network which supplies power to various loads. Such loads may be, for example, various power machines.

In such arrangements, utilities need to measure power coming out of the generating station or going into a power station. It is also important to minimize the phase relationship between the current and voltage waveforms of the power being transmitted to minimize losses. Thus, accurate measurement of these waveforms is important.

In industrial applications, it is important to continuously monitor the voltage, current and phase of the power into the machine. These parameters may vary with the machine load. With knowledge of these parameters the industrial user can better adjust, and control the loads to control machines, determine alarm conditions and/or to more efficiently use the power.

Various different arrangements are presently available for monitoring, measuring, and controlling power parameters. Typically, an individual power measuring device which measures specific power system parameters is placed on a given branch or line proximate one of the loads. Such power monitoring devices measure electrical power parameters, such as those described above.

An example of such a system is disclosed in U.S. Pat. No. 5,151,866. In the system disclosed in this patent, a power analyzer system uses discrete analog transducers to convert AC voltage and current signals from a power system to DC output signals. The values from the voltage and the current transducers are then used to calculate the various other desired power parameters.

In addition to monitoring power parameters of a certain load, power monitoring devices have a variety of other applications. For example, power monitoring devices can be used in supervisory control and data acquisition systems (SCADA), process controllers (PLC), etc.

As discussed briefly above, in industrial applications, a plurality of the power monitoring units are placed on the branches of a power distribution system near the loads. The monitoring units are connected through a communication network to at least one central computer. An example of such system is disclosed in Siemens Power Engineering & Automation VII (1085) No. 3, Pg. 169, Microprocessor--Based Station Control System For New And Existing Switchgear, Muller et al.

In fact, many other applications also use a network of devices interconnected through some sort of communication media. Often, the network is composed of a large number of slave devices with a much smaller number of master devices. A master device is any device that can query another device or change the configuration of another device. A slave device is a device that performs a function, and produces results that can be accessed by another device. It is possible for a single device to act as a master and a slave. In the power monitoring system described above, the central computer is the master device and the individual power monitoring units are the slave devices.

The architecture of the slave devices is such that they contain a large number of registers. Some of these registers contain output values from the slave device which can be read by the master and some of these registers contain setup information for the slave device which the master can read or write. The master device must know which registers contain which information for every different slave device. For instance the master device would know that a certain device measures volts and it would know that volts are stored in a particular register. Therefore, in order for the master to retrieve a reading of volts from the slave device it must send a request (communications packet) to the slave device indicating that it requires a packet containing the number in the respective register.

With this approach, the master device(s) must have a large amount of knowledge about the configuration of the remote devices. This requires large amounts of storage space on the master device(s). Also, if the characteristics of a slave device are changed, or a new type of slave device is added, the master device(s) must be reprogrammed. If the slave devices go through a large number of changes, the master device(s) must retain information about the slave devices for all intermediate versions to retain backward compatibility. This further increases the memory and processing power requirement for the master device(s).

In the configuration where the slave device is field programmable, the master device(s) must have some means of determining the slave device's current configuration. In addition the master device(s) must be able to change the slave device's configuration. This invariably means that the master device(s) must know all the possible configurations of the remote device which again increases the memory and processing power required for the master device.

Further, if there are multiple masters changing the configuration of the same slave device, it is difficult for the masters to keep track of the current configuration of the device. Each master has its own local copy of the current configuration of the slave device. When another master changes the configuration of the device, the first master's local copy is not updated. Thus, the first master may think the device is executing a function it no longer is.

If the configuration of a slave device is not configurable or if the slave device has limited configurability, the slave device may be using its available resources (memory and processing power) to perform functions that the user has no interest in. Therefore, the slave device may perform many functions that are not required, but may be missing some functions that are required by a certain user.

Systems are available which use an object oriented approach to program a computer to connect the outputs of a number of remote devices to local functions on the computer and to the inputs of other devices. U.S. Pat. Nos. 4,901,221, 4,914,568 and 5,155,836 disclose such systems where a central digital computer is connected to a number of remote devices. In the systems disclosed in these patents, however, the object oriented structure resides on the central digital computer and all information must travel through the central computer. Therefore, the speed of the system is limited to the speed of the communications channels between the computer and the remote devices and the speed of the computer. Further, although the structure on the computer can be modified through the object oriented architecture the slave devices cannot be easily modified or updated.

Systems are also available which allow reprogramming of a slave device. For example, such a system is disclosed in U.S. Pat. No. 5,155,836. The controlling logic within these devices, however, does not allow the reconfiguration of the device while other functions within the device continue to operate. The user must compile and download firmware in order to implement a different control program. The downloading process interrupts the operation of the device.

Therefore, in view of the above it is a primary object of the present invention to provide a power monitor which can be readily configured to exactly match a user's unique requirements.

It is a further object of the present invention to provide a power monitoring system where it is not necessary to change the software on a master device when a slave device is upgraded.

It is a further object of the present invention to provide a power monitoring system where the storage space memory and/or processing power required for master device(s) is minimized.

It is still a further object of the present invention to provide a power monitoring system where master device(s) can accurately and easily track changes or modifications in the configuration of individual monitoring units devices.

SUMMARY OF THE INVENTION

To achieve these and other objectives, the present invention uses an object oriented architecture within individual digital devices, such as monitoring devices. The monitoring devices include circuitry which receives an electrical signal and generates at least one digital signal representing the electrical signal. Objects within such individual monitoring units include modules which perform a function and preferably registers which contain the inputs, outputs and setup information for the modules. Methods can be invoked on all objects to change or query the operation or configuration of the device. At least one of the modules receives the digital signal as an input and uses the signal to generate measured parameters. Additional modules take measured parameters as input and generate additional parameters therefrom.

In one preferred embodiment, the monitoring device includes transducers which measure voltage and current from a power line.

In another preferred embodiment, a flow controller is used to control the operation of the modules. A feature manager provides a means for accessing the entire device.

Since, the objects reside inside the individual slave devices the communication between the different objects is limited only by the processing speed of the individual monitoring units and not by the speed of the communications media between the devices. With this arrangement the number of slave devices connected to a single master is virtually unlimited since no communication between the devices is required unless a specific request from the user is made.

The operations that the monitoring unit performs are configured by a master device executing methods which instruct the monitoring unit to connect modules to registers. The objects can be programmed and linked in totally arbitrary ways, enabling the user to build arbitrary functional blocks consisting of networks of objects.

Many modifications to the preferred embodiment will be apparent to those skilled in the art. It is the intention of this description to provide an example system using the invention. It is not the intention of this description to limit the scope of the invention.

BRIEF DESCRIPTION OF THE DRAWINGS

FIG. 1 schematically represents a preferred embodiment of a system using a power monitoring unit of the present invention.

FIG. 2 schematically illustrates a preferred embodiment of a physical layout of a preferred embodiment of a system of the present invention.

FIG. 3 schematically illustrates a preferred embodiment of the internal structure of a power monitoring unit of the present invention.

FIG. 4 schematically illustrates a preferred embodiment of the data acquisition module and its respective registers.

FIG. 4A shows a flowchart of a preferred embodiment of the logic for the client portion of the data acquisition module.

FIG. 5 schematically illustrates a preferred embodiment of the power meter module and its respective registers.

FIGS. 5A-5L show flowcharts of a preferred embodiment of the logic for the client portion of the power meter module.

FIG. 6 schematically illustrates a preferred embodiment of the analog input module and its respective registers.

FIG. 6A shows a flowchart of a preferred embodiment of the logic for the client portion of the analog input module.

FIG. 7 schematically illustrates a preferred embodiment of the analog output module and its respective registers.

FIG. 7A shows a flowchart of a preferred embodiment of the logic for the client portion of the analog output module.

FIG. 8 schematically illustrates a preferred embodiment of the digital input module and its respective registers.

FIGS. 8A-8B show a flowchart of a preferred embodiment of the logic for the client portion of the digital input module.

FIG. 9 schematically illustrates a preferred embodiment of the digital output module and its respective registers.

FIGS. 9A-9H show a flowchart of a preferred embodiment of the logic for the client portion of the digital output module.

FIG. 10 schematically illustrates the inheritance of the registers and modules.

FIG. 10A schematically illustrates the inheritance of some of the registers.

FIG. 10B schematically illustrates the inheritance of some of the modules.

FIG. 10C illustrates a hierarchical structure.

FIG. 11 schematically illustrates a preferred embodiment of the properties of the modules.

FIG. 12 schematically illustrates a preferred embodiment of the data flow for a module.

FIGS. 12A-12C show a flowchart of a preferred embodiment of the logic for the module operation.

FIG. 13 schematically illustrates a preferred embodiment of the AND/OR module and its respective registers.

FIGS. 13A-13B show a flowchart of a preferred embodiment of the logic for the client portion of the AND/OR module.

FIG. 14 schematically illustrates a preferred embodiment of the Setpoint module and its respective registers.

FIGS. 14A-14C show a flowchart of a preferred embodiment of the logic for the client portion of the setpoint module.

FIG. 15 schematically illustrates a preferred embodiment of the EventLog module and its respective registers.

FIG. 15A shows a flowchart of a preferred embodiment of the logic for the client portion of the EventLog module.

FIG. 16 shows an example application using the object oriented structure of this invention.

FIGS. 17A-17B show the operation of the Module Flow Controller.

FIG. 18 schematically illustrates a preferred embodiment of the analog output manager.

FIGS. 18A-18B show a flowchart of a preferred embodiment of the logic for the application of a manager.

FIG. 19 schematically illustrates a preferred embodiment of the feature manager.

FIGS. 19A-19B show a flowchart of a preferred embodiment of the logic for the server portion of the feature manager.

FIGS. 20A-20C show a flowchart of a preferred embodiment of the logic for the operation of a boolean register.

FIGS. 21A-21B show a flowchart of a preferred embodiment of the logic for the operation of an enumerated register.

FIGS. 22A-22B show a flowchart of a preferred embodiment of the logic for the operation of a numeric register.

FIGS. 23A-23B show a flowchart of a preferred embodiment of the logic for the operation of a numeric bounded register.

DETAILED DESCRIPTION OF THE PRESENTLY PREFERRED EMBODIMENTS

The present invention comprises a novel system with an object oriented structure. The novel system and architecture are particularly useful for configuring a power monitoring unit to perform given functions and causing the unit to execute those functions.

FIG. 1 schematically illustrates how a power monitoring unit 100 using the present invention is connectable to a three wire power line. Three current transducers (CTs) 102A, 102B and 102C are connected to wires 101A, 101B and 101C of the power line, respectively. Potential transducers (PTs) 104A and 104B are connected between lines 101A, 101B and 101B, 101C, respectively. A plurality of fuses 106 are disposed between the lines 101A-101C and Pts 104A and 104B. Fuses 110 are connected between Pts 104A and 104B and unit 100.

The CTs 102A-102C are connected through a shorting switch or test block 108 to the power monitoring unit 100. The CTs 102A-102C provide the power monitoring unit 100 with current inputs I11-I32. The PTs 104A and 104B provide the power monitoring unit 100 with voltage inputs V1-V3. Current inputs I41 and I42, chassis ground 112 and voltage input VREF are connected to ground potential. The unit 100 is connected to a power supply, such as a standard 120 V AC supply, through power leads L and N.

FIG. 2 shows a preferred embodiment of the physical layout of a plurality of monitoring units 100 in a system using the present invention. The system comprises one or more personal computers (PCs) 114 which are used as master devices. A plurality of monitoring units 100 configured as intelligent electronic devices (IEDs) are used as slave devices. Virtual intelligent electronic devices (VIEDs) 115 which reside in software on the personal computer 114 can also serve as slave devices. All devices in the system are interconnected through a communication network 116. The network may be directly connected to devices or may connect through other communications devices such as modems 120. Preferably, the IEDs, PCs and VIEDs all have an object oriented architecture as described in detail below.

To fully appreciate the present invention, an understanding of the principals of basic object oriented structures is necessary. Therefore, a brief description of the type of architecture is given here. (A more detailed discussion of the principles of object oriented structures is given in "SMALLTALK-80 The Language And Its Implementation," Goldberg and Robson, 1983 (from which some of the following definitions are taken)). An object consists of some private memory and a set of operations. An object has state, behavior and identity. The nature of the object's operations depends on the type of component it represents. For example, objects representing numbers compute arithmetic functions, and objects representing data structures store and retrieve information. A key component of object oriented architecture is encapsulation. Encapsulation is the process of hiding all of the details of an object, as well as the implementation of its methods. In an object oriented system, in order for an object to carry out one of its operations, a request must be made which specifies which operation is desired. The request is called a "message". Importantly, because of encapsulation in object oriented architecture, the message does not specify how that operation is to be carried out. The "receiver", the object to which the message was sent, determines how to carry out the requested operation. The set of messages to which an object can respond is called its "interface" with the rest of the system. The only way to interact with an object is through its interface. A crucial property of an object is that its private memory can be manipulated only by its own operations. Messages are the only way to invoke an object's operations. These properties ensure that the implementation of one object cannot depend on the internal details of other objects, only on the messages to which they respond.

Messages ensure the modularity of the system because they specify the type of operation desired, but not how the operation should be accomplished.

Other important components of object oriented architecture are "classes" and "instances". A class describes the implementation of a set of objects that all represent the same kind of component. The individual objects described by a class are called its instances. A class describes the form of its instances' private memories and it describes how they carry out their operations. Even an object that represents a unique component is implemented as a single instance of a class. The instances of a class are similar in both their public and private properties. An object's public properties are the messages that make up its interface. All instances of a class have the same message interface since they represent the same kind of component. An object's private properties are a set of instance variables that make up its private memory and a set of methods that describe how to carry out its operations. The instance variables and methods are not directly available to other objects. The instances of a class all use the same set of methods to describe their operation.

Each method in a class tells how to perform the operation requested by a particular type of message. When that type of message is sent to any instance of the class, the method is executed. A class includes a method for each type of operation its instances can perform. The method may specify some changes to the object's private memory and/or some other messages to be sent. A method also specifies a value that should be returned. An object's methods can access the object's own instance variables, but not those of any other objects.

Another important aspect of the objects within the device is that they are independent or autonomous. In other words, any change in the configuration of one object on a slave by a master device does not affect the operation of the other objects on the slave device (or any objects on the master device).

Referring now to FIG. 3, a preferred embodiment of the internal structure of an IED 100 is illustrated. As described in more detail below, the IED's 100 are run by an object oriented structure. The electrical signals (i.e. the voltage and current) from the power lines are used by a detector to generate digital signals which represent the electrical signals. In the illustrated embodiment, the detector is comprised of the CTs 102, PTs 104, conditioning circuitry and A/D converters, as described more fully below. Three-phase voltage and current input signals V1-V3 and I1-I4 from electric power lines enter the motherboard 25 and are converted to voltage levels compatible with the analog to digital converters (A/Ds) 29 and 30 by signal conditioning circuitry 23. In an exemplary embodiment a suitable A/D convertor is a 13 bit, 7 input one available from National Semiconductor as model No. LM12458. A suitable voltage to the A/D's 29 and 30 ranges from 0 to 5 Volts depending on what part of the AC signal the sample is taken at and the level of the AC signal.

In the illustrated embodiment, the signal conditioning circuitry comprises operational amplifiers (op amps) 60, 62 and 64 and associated circuitry which amplify V1, V2 and V3 respectively. The currents I1, I2, and I3 are amplified by two different scales to provide greater dynamic range. The amplification to the two different scales is implemented using the conditioning circuitry 23. Op amps 66A, 66B and 66C amplify input current signals I1, I2 and I3, respectively, to a first scale. For example, a current of 5 Amperes AC creates a voltage of 4 Volts AC to the A/D converter. Op amps 68A, 68B and 68C amplify input current signals I1, I2 and I3, respectively to a second scale. For example, a current of 100 Amperes AC creates a voltage of 4 Volts AC to the A/D converter. The voltage and current signals enter separate A/Ds 29 and 30 so that the voltage and current on a particular phase can be simultaneously sampled. Auxiliary Input Signals 20 on the AUX board 24 also pass through signal conditioning circuitry 22 and to A/D 29. Auxiliary inputs allow the user to sample additional signals in addition to the three-phase voltage and current. For example, the auxiliary inputs may be 0 to 10 Volts DC outputs from a temperature transducer.

A digital signal processor (DSP) 28 reads the samples from the A/D converters 29, 30 through the A/D Bus 31. The signals are preferably sampled at the rate of 128 samples per line frequency cycle. The DSP performs a Fast Fourier Transform (FFT) on the samples to determine the frequency components of the signal in a manner known in the art. It also calculates Root Mean Square (RMS) voltage and/or current for each input signal. This data is then transferred through dual port RAM 27 to the microcontroller 35. A suitable DSP is a 4K byte RAM available as a TMS320C25 available from Texas Instruments.

The microcontroller 35 performs many functions within the IED. The fundamental frequency to square wave converter 43 provides a square wave at the fundamental frequency of the incoming voltage signals. A suitable fundamental frequency to square wave converter is an LM311D available from National Semiconductor configured in a manner known in the art. A time processing unit (TPU) within the microcontroller 35 measures this frequency and multiplies it by a predetermined value, such as 128. The TPU creates an A/D sample clock 42 at this new frequency so that the A/Ds sample at 128 samples per cycle. A suitable microcontroller is a MC68332ACFC16 available from Motorola.

Different AUX boards 24 and motherboards 25 can be exchanged with different CPU Boards 46. This, however presents a calibration problem. In the system of the present invention, the calibration information for the circuitry 22, 23 of each AUX or motherboard is preferably stored on the individual board. A suitable EEPROM in a 93LC56 available from Microchip. This is implemented by storing the information in calibration constants EEPROM 39, 40 on each individual board. The microcontroller 35 then reads the information using the synchronous serial communications bus 38 before performing calculations on the values received through the dual port RAM 27 from the DSP 28. The synchronous serial communications bus 38 is also used to communicate with the display 51. Results of all calculations and control functions of the microcontroller 35 can be displayed on the display.

The IED 100 connects to the network 116 through the communications board 48. The microcontroller 35 sends and receives information over the serial communications bus 47.

A further description of a preferred embodiment of the present invention and its operation is given in U.S. patent application Ser. No. 08/367,534 filed concurrently with this application and entitled "High Accuracy Power Monitor and Method" which is incorporated herein by reference.

FIGS. 4, 5, 6, 7, 8 and 9 show how the auxiliary input signals 20, the voltage and current input signals 21, and the digital I/O signals 44 may be represented in the object oriented structure of this invention. In an exemplary embodiment, in the IED 100 the logic or code is implemented in firmware and in the PC the code is implemented in software. It will, of course, be recognized by those skilled in the art that the logic for the IED 100 can also be implemented in software and that the logic in the PC can be implemented in firmware. In the present embodiment, the firmware is implemented using a 512K byte flash EEPROM 34 available from Intel as a 28F010 EEPROM. In an exemplary embodiment, the software is written in the C programming language. An exemplary embodiment of the logic for the object oriented architecture of the present invention in object code is given in microfiche Appendix A which is incorporated herein by reference. The object code is presented in Srecord format which is defined in the M68332BUG Debug Monitor User's Manual (Motorola 1990) which is incorporated herein by reference. More detailed schematics for the presently preferred embodiment are given in microfiche Appendix B which is incorporated herein by reference.

In the system of the present invention, two fundamental classes exist for objects: 1) registers and 2) modules. Both the registers and modules are derived from a common base class (class=1). The registers are passive data storage objects containing a single value, an array or structure. Registers behave only as "servers" in the architecture. A "server" is defined as an entity which can respond to method invocations. A "client", on the other hand, is an entity which can invoke a method on a server. Modules behave both as client and server. The client portion of the module contains the active components that perform the various tasks within the device. The inheritance of the registers and modules is shown in FIG. 10. An inheritance diagram for some of the registers is shown in FIG. 10A. An inheritance diagram for some of the modules is shown in FIG. 10B. Data passing between objects is accomplished using method invocation using "types," where types define the semantics for passing data between objects. A method is invoked by a "client" sending a message to another object. This message contains a "method" and may contain a "value". Every method in an object has a security level. Any methods which are invoked with a level less than the security level for that method will fail. The system also has the following set of rules of operation which must be followed by objects:

1. All data passed to or from an object must have a Type.

2. Modules must be owned by a module, with the exception of the root module, which has no owner.

3. Registers must be owned by a module.

4. Behavior of servers will be consistent for multiple clients.

5. A server portion of a object cannot access the server portion of another object.

6. A client portion of an object cannot access the client portion of another object.

7. Any register or module cannot be destroyed if it is owned by any module.

The system also has a hierarchy. As used herein a hierarchy means that every manager, module and register can be accessed by starting at the top of the hierarchy. This concept can be seen pictorially by referring to FIG. 10C. In this figure modules or registers that appear as setup registers are connected to the bottom of the modules or managers with a line. Registers that appear as output registers are connected with lines to the right side of the modules and registers that appear as input registers are connected with lines to the left of the modules.

Certain semantics are needed for passing information to and from modules and registers. Here these semantics are defined by "Types". Table A provides the Types defined in the presently preferred embodiment.

                                      TABLE A                                      __________________________________________________________________________     The Types describe the semantics for passing information to and from           modules and registers.                                                         Type Name    Type equivalence  Restrictions                                                                               Description                         __________________________________________________________________________     VoidType     fundamental Type              Has no semantic                                                                value.                              SignedType   fundamental Type  Maximum size =                                                                             Defines a signed                                                   32 bits.    value.                              UnsignedType fundamental Type  Maximum size =                                                                             Defines an                                                         32 bits     unsigned value.                     CharType     fundamental Type  Maximum size =                                                                             Defines a                                                          32 bits.    character value.                                                               Supports wide                                                                  characters as                                                                  well as ASCII.                      BooleanType  fundamental Type  Size = 1 bit.                                                                              Defines a                                                                      Boolean value.                                                                 Value may be                                                                   TRUE or FALSE.                      FixedPointType                                                                              fundamental Type  Maximum size =                                                                             Defines a fixed                                                    64 bits.    point value.                        FloatType    fundamental Type  Size = 32, 64, or                                                                          Defines a floating                                                 80 bits.    point value.                        ComplexType  fundamental Type  Maximum size =                                                                             Defines a                                                          TBA.        complex value.                      DeltaType    fundamental Type  Size = 0 bits.                                                                             The value                                                                      represents a                                                                   delta-function                                                                 pulse.                              RealType     define union RealType =       Defines a real                                   SignedType.linevert split.    value.                                           UnsignedType.linevert split.                                                   CharType.linevert split.                                                       BooleanType.linevert split.                                                    FloatType.linevert split.                                                      FixedPointType.                                                   NumericType  define union                  Defines a                                        NumericType =                 numeric value.                                   RealType.linevert split.                                                       ComplexType.                                                      SignedArrayType                                                                             define array                  Defines an array of                              SignedArrayType =             signed values.                                   {SignedType                                                                    `value.sub.i `}.                                                  UnsignedArrayType                                                                           define array                  Defines an array of                              UnsignedArrayType =           unsigned values.                                 {UnsignedType `value.sub.i `}.                                    CharArrayType                                                                               define array CharArrayType =  Defines an array of                              {CharType `char.sub.i `}.     characters.                         BooleanArrayType                                                                            define array                  Defines an array of                              BooleanArrayType =            Boolean values.                                  {BooleanType `value.sub.i `}.                                     FixedPointArrayType                                                                         define array                  Defines an array of                              FixedPointArrayType =         fixed point values.                              {FixedPointType `value.sub.i `}.                                  FloatArrayType                                                                              define array FloatArrayType = Defines an array of                              {FloatType `value.sub.i `}.   floating point values.              ComplexArrayType                                                                            define array                  Defines an array of                              ComplexArrayType =            complex values.                                  {ComplexType `value.sub.i `}.                                     NumericArrayType                                                                            define union                  Defines an array of                              NumericArrayType =            numeric values.                                  SignedArrayType.linevert split.                                                UnsignedArrayType.linevert split.                                              CharArrayType.linevert split.                                                  BooleanArrayType.linevert split.                                               FixedPointArrayType.linevert split.                                            FloatPointArrayType.linevert split.                                            ComplexArrayType.                                                 ArrayUnsignedArray                                                                          define structure              Structure defines an                Type         ArrayUnsignedArrayType =      array of                                         {UnsignedArrayType            UnsignedArrayTypes.                              `us.sub.-- array.sub.i `}.                                        StringType   define StringType =                                                                              must be null terminated.                                                                   Defines a character                              CharArrayType.                string (null-terminated).           StringArrayType                                                                             define structure              Defines an array of                              StringArrayType =             strings.                                         {CharArrayType `string.sub.i `}.                                  SizeType     define SizeType =             An unsigned integral                             UnsignedType.                 value which is used for                                                        defining a size                                                                parameter (e.g. size of                                                        array, #records).                   CounterType  define CounterType =          An unsigned integral                             UnsignedType.                 value which can be                                                             incremented (by 1 or                                                           more), decremented (by                                                         1 or more), and cleared                                                        to 0.                               IndexType    define IndexType =            An unsigned integral                             UnsignedType.                 value which is used to                                                         index arrays.                       TimeType     define TimeType =             Universal Time (GMT) in                          NumericType.                  seconds.                            ReasonType   define ReasonType =           The reason for an                                CharArrayType.                exception.                          ExceptionType                                                                               define structure ExceptionType =                                                                             An exception returns a                           UnsignedType                  code and value. A                                `exception.sub.-- cause.      reason string is                                 Type                          opitonal.                                        `exception.sub.-- value`      The valid codes are:                             [ReasonType `reason`].        0 = underflow                                                                  1 = overflow                                                                   2 = not.sub.-- valid                                                           3 = not.sub.-- supported                                                       4 = not.sub.-- available                                                       5 = invalid.sub.-- method                                                      6 = loss.sub.-- of.sub.--                                                      precision.                                                                     7 = internal.sub.-- error           MethodType   define                        The value represents                             MethodType=UnsignedType.      (numerically) the                                                              particular method of an                                                        Object.                             ClassType    define ClassType =            The value represents                             UnsignedType.                 (numerically) a particular                                                     class (such as Numeric                                                         Register of PowerMeter                                                         Module).                            NodeHandleType                                                                              define union NodeHandleType = An address to a remote                           StringType.linevert split.    IED site.                                        UnsignedType.                                                     ExtendedHandleType                                                                          define structure              Defines a handle used                            ExtendedHandleType =          to a reference an object                         [NodeHandleType`node`]        on another IED.                                  UnsignedType `handle`.                                            HandleType   define union HandleType =     The value represents                             UnsignedType.linevert split.  the address of an                                ExtendedHandleType.           object.                             ExtendedHandle                                                                              define structure array        The value is an array of            ArrayType    ExtendedHandleArrayType =     Extended Handles.                                {ExtendedHandle `value.sub.i `}.                                  HandleArrayType                                                                             define union HandleArrayType =                                                                               The value is an array of                         ExtendedHandleArrayType.linevert split.                                                                      handle values.                                   UnsignedArrayType.                                                PriorityType define            Priorities range from 0                                                                    The value represents an                          PriorityType = UnsignedType.                                                                     to 255      priority. Guidelines for                                                       priorities are as follows:                                                     Urgent                                                                         192 to 255                                                                     High                                                                           128 to 191                                                                     Medium 64 to 127                                                               Low 0                                                                          to 63                               RangeType    define structure RangeType =  defines a range of                               IndexType                     values that starts at                            `range.sub.-- start`          index range.sub.-- start and                     IndexType                     ends at index                                    `range.sub.-- end`.           range.sub.-- end. This is                                                      useful in log situations.           EventType    define structure EventType =  Defines a structure for                          PriorityType `priority`       an event.                                        UnsignedType                  Values for event.sub.-- state                    `event.sub.-- state`          are:                                             HandleType                    0 = unary state event.                           `cause.sub.-- handle`         1 = Active transition                            IONType                       for bi-state event.                              `cause.sub.-- value`          2 = Inactive transition                          HandleType                    for bi-state event.                              `effect.sub.-- handle`        3 = Label change                                 IONType                       event.                                           `effect.sub.-- value`.                                            LogHeaderType                                                                               define                        Structure defines the                            LogHeaderType =               header for a general                             HandleArrayType               purpose log record.                 LogRecordType                                                                               define structure LogRecordType =                                                                             Structure defines the                            IndexType `position`          data values in a general                         TimeType                      purpose log record.                              `timestamp`                                                                    {Type `value.sub.i `}.                                            LogArrayType define structure.sub.-- array Array of log records.                            LogArrayType =                                                                 {LogRecordType `logrec.sub.i `}.                                  WaveformType define structure              Defines a structure for                          WaveformType =                a waveform.                                      NumericType                   Note:                                            `sampling.sub.-- frequency`   plotted value =                                  NumericType `offset`          (data point +                                    NumericType `scale`           offset) * scale.                                 TimeType                                                                       `time.sub.-- of.sub.-- first.sub.-- point`.                                    NumericArray `points`.                                            AlarmType    define structure AlarmType =  Structure for alarms:                            HandleType                    When parameter                                   `effect.sub.-- handle`        Transitions is odd the                           CounterType                   alarm is active.                                 `transitions`.                                                                 PriorityType `priority`.                                          AlarmArrayType                                                                              define structure.sub.-- array Array of alarms.                                 AlarmArrayType =                                                               {AlarmType `alarm.sub.i `}.                                       SecurityType define                        Value represents a                               SecurityType = UnsignedTypes. security level.                                                                The following security                                                         levels are defined:                                                            1 = no access                                                                  16 = user (R/O)                                                                32  = user (R/W)                                                               48 = configure (can                                                            create/destroy                                                                 modules)                                                                       64 = system                                                                    administration (can                                                            change secruity                                                                levels).                                                                       80 = highest level                                                             (factory - i.e. cal                                                            constants)                          MehtodSecurityType                                                                          define structure              Assigns a security level                         MethodSecurityType =          to a method.                                     MethodType `method`                                                            SecurityType `security`.                                          MethodSecurityArray                                                                         define structure.sub.-- array Array of method-                    Type         MethodSecurityArrayType =     security.                                        {MethodSecurityType                                                            `methsec.sub.i `}.                                                CompositeLogRecord                                                                          define structure              This is the complete                             CompositeLogRecord =          description of a log                             UnsignedType                  record.                                          `record.sub.-- type`          Note:-the position field                         HandleType `handle`           of the log record type is                        LogHeaderType `header`        the record ID.                                   [StringArrayType `labels`]    RecordType is currently                          LogArrayType `records`.       always zero.                        CompositeLogArray                                                                           define structure.sub.-- array An array of                                      CompositeLogArray =           CompositeLogRecords                              {CompositeLogRecord                                                            `record.sub.i `}.                                                 CompositeEventRecord                                                                        define structure              This is a complete                               CompositeEventRecord =        description of a single                          UnsignedType                  event (either unary                              `record.sub.-- type`          event or half of a                               HandleType `handle`           binary event). The                               LogHeaderType `header`        header consists of two                           [StringArrayType `labels`]    handles cause.sub.-- handle                      LogArrayType `records`        and effect.sub.-- handle (in                     TimeType                      this order).                                     `achmowledge.sub.-- time`     The records field                                PriorityType `priority`.      always has two                                                                 elements, cause.sub.-- value                                                   and effect.sub.-- value.                                                       RecordType is 0 for                                                            unary events, 1 for                                                            binary active events, 2                                                        for binary inactive                                                            events, and 3 for label                                                        change events.                      CompositeEventArray                                                                         define structure              An array of                                      CompositeEventArray =         CompositeEventRecords                            {CompositeEventRecord                                                          `record.sub.i `}.                                                 PredicateOperator                                                                           define PredicateOperatorType =                                                                   Defines some SQL                                Type         UnsignedType `operator`.      predicate operators                                                            0 = AND                                                                        3 = OR                                                                         1 = IN                                                                         4 = XOR                                                                        2 = BETWEEN                         PredicateOperand                                                                            define PredicateOperandType = A predicate for an SQL-             Type         Type `operand`                type query is formed                                                           from a list of                                                                 PredicateOperandType                                                           (see SearchCriteria                                                            type).                                           SortOrderType     define structure SortOrderType                                                             order is:                                        UnsignedType `order`          0 = Ascending order                              StringType `key`.             1 = Descending order.                                                          key names a key field                                                          of a table.                         SortOrderArray                                                                              define structure.sub.-- array                                                  SortOrderArray =                                                               {Sort OrderType                                                                `order.sub.i `}.                                                  SearchCriteria                                                                              define structure SearchCriteria =                                                                            Defines a query on a                             {PredicateOperandType         LogSchemeRegister                                `operand.sub.i }              The list of operands                                                           form a predicate in                              SortOrderArray `order`.                                                                          postfix (reverse Polish)                                                                   notation.                           Type         define union Type =           All Types.                                       /* type all types here */                                         __________________________________________________________________________      Note:                                                                          Arrays of fundamental Types are defined as "array" but arrays of               nonfundamental Types ase defined as "struturearray". This distinction          improves communication throughput in the system.                         

Table 1 lists a set of methods which are presently defined for the base class. All of these base class methods are inherited by the registers and modules.

                                      TABLE 1                                      __________________________________________________________________________     #  Method        Return-type                                                                            Description                                           __________________________________________________________________________     1  read.sub.-- class( )                                                                         ClassType                                                                              Causes a manager, module or register to return                                 a                                                                              number indicating what type of manager, module                                 or                                                                             register it is.                                       2  read.sub.-- name ( )                                                                         StringType                                                                             Causes a manager, module or register to return                                 a                                                                              string containing the name of the manager,                                     module or                                                                      register.                                             3  read.sub.-- label ( )                                                                        StringType                                                                             Causes a manager, module or register to return                                 a                                                                              string containing the label for the manager,                                   module or                                                                      register. A label differs from a name in that it                               can                                                                            be programmed by executing a Write Label method                                on                                                                             the manager, module or register. If no label is                                programmed the object name will be returned.          128                                                                               write.sub.-- label(StringType)                                                               BooleanType                                                                            Write the programmable object label. If a                                      null-string is                                                                 written, the Label is destroyed.                      129                                                                               read.sub.-- security.sub.-- level(                                                           SecurityType                                                                           Is executed to determine whether a method can                                  be                                                       MethodType)           executed on a particular manager, module or                                    register.                                                                      Not all methods are available on all devices.                                  The                                                                            master device can determine whether it will                                    receive a                                                                      valid result by first executing this method.                                   Another                                                                        method, Read All Security Levels returns a list                                which                                                                          corresponds to the security levels of all the                                  methods                                                                        that can be executed on a manager or module.          130                                                                               read.sub.-- all.sub.-- security.sub.-- levels( )                                             MethodSecurity                                                                         Read the security levels for all methods of a                                  given                                                                  ArrayType                                                                              object. Only methods valid for the object's                                    class are                                                                      included.                                             131                                                                               read.sub.-- parent.sub.-- handle                                                             HandleType                                                                             Returns a handle of the parent of a manager,                                   module                                                                         or register. For instance, executing this method                               on an                                                                          analog output module will return the handle of                                 the                                                                            analog output manager. Executing this method on                                the                                                                            analog output manager will return a handle to                                  the                                                                            feature manager. Executing this method on an                                   analog                                                                         output's output register returns the analog                                    output                                                                         module.                                               132                                                                               read.sub.-- owners( )                                                                        HandleArray                                                                            Returns a list of handles for all the modluels                                 that own                                                               Type    the object this method is executed on. This                                    will                                                                           include a list of modules if the method is                                     invoked on a                                                                   register or a manager if it is invoked on a                                    module.                                               133                                                                               IsA(ClassType)                                                                               BooleanType                                                                            Returns a value indicating whether or not and                                  object is                                                                      derived from the class given as an argument.          134                                                                               check.sub.-- sanity( )                                                                       BooleanType                                                                            Checks to see if the manager, module or register                               is                                                                             operating correctly. i.e., determines whether                                  the                                                                            software that implements the object is                                         operating                                                                      correctly. Returns True if object is                  __________________________________________________________________________                              sane.                                            

If a method invocation is unsuccessful, an ExceptionType will be returned rather than the normal Return-type.

In the current implementation a module performs a function using registers. Input registers provide the information a module is operating on. Setup registers permit modification of the operation of the module. Output registers contain the results of the module's operation. The output registers of one module can be used as input registers for another. The module keeps track of which registers are to be used for its input, output and setup. The links to the input registers can be modified, but those to the output and setup registers are fixed. A module is said to "own" all the registers it is linked to. Methods may also be executed on registers once the handle to a register is known. The handle of a register or module is a number which is unique for each register and module on a device. When a method is invoked, a handle is supplied which indicates which module or register the method is to be invoked upon.

In most instances, the methods that can be invoked on the different types of registers depend on what type of register is involved. Table 2 lists a set of methods which are presently defined for all registers (all register classes are inherited from the register class).

                  TABLE 2                                                          ______________________________________                                         Register Class (R) - class = 20                                                #   Method          Return-type                                                                               Description                                     ______________________________________                                         20  read.sub.-- time( )                                                                            TimeType   Read the time of last                                                          update.                                         21  read.sub.-- value( )                                                                           VoidType   Read the value of the                                                          object                                          22  write.sub.-- value(VoidType)                                                                   BooleanType                                                                               Write the value of the                                                         object                                          ______________________________________                                    

TABLES 3-19 list methods which are supported for the indicated register classes. (In Tables 3-19, "*" indicates that the method is inherited from the parent class and "+" indicates that the method is re-defined from the parent class.)

                                      TABLE 3                                      __________________________________________________________________________     BooleanVariableRegister (BVR) - class = 21                                     This class defines a Boolean variable storage location.                        #  Method        Return-type                                                                          Description                                             __________________________________________________________________________     20 read.sub.-- time( )*                                                                         TimeType                                                                             Read the time of last update                            21 read.sub.-- value( )+                                                                        BooleanType                                                                          Read the value of the register.                         22 write.sub.-- value(BooleanType)+                                                             BooleanType                                                                          Write the value of the register                         30 read.sub.-- ON.sub.-- label( )                                                               StringType                                                                           Read the ON label.                                      500                                                                               write.sub.-- ON.sub.-- label(StringType)                                                     BooleanType                                                                          Write the ON label.                                     31 read.sub.-- OFF.sub.-- label( )                                                              StringType                                                                           Read the OFF label.                                     501                                                                               write.sub.-- OFF.sub.-- label(StringType)                                                    BooleanType                                                                          Write the OFF label.                                    32 read.sub.-- current.sub.-- state.sub.-- label( )                                             StringType                                                                           Returns the ON label if register value =                                       True and OFF label if register value =                                         False.                                                  __________________________________________________________________________

                                      TABLE 4                                      __________________________________________________________________________     EnumeratedRegister (ENR) - class = 22                                          This class defines a register that can store one instance of an                enumerated list.                                                               #  Method      Return-type                                                                            Description                                             __________________________________________________________________________     20 read.sub.-- time( )*                                                                       TimeType                                                                               Read the time of last update                            21 read.sub.-- value( )+                                                                      StringType                                                                             Read the value of the register.                         22 write.sub.-- value(StringType)+                                                            BooleanType                                                                            Write the value of the register. The string must                               be one of the strings provided by the                                          read.sub.-- unumerations( ) method - otherwise                                 the                                                                            method will fail.                                       520                                                                               read.sub.-- enumerations( )                                                                StringArrayType                                                                        Read the enumeration list. This list contains                                  ALL possible register values.                           __________________________________________________________________________

                  TABLE 5                                                          ______________________________________                                         NumericRegister (NR) - class = 24                                              This is the parent class for Numeric Registers.                                #   Method           Return-type                                                                               Description                                    ______________________________________                                         20  read.sub.-- time( )*                                                                            TimeType   Read the time of                                                               last update                                    21  read.sub.-- value( )+                                                                           NumericType                                                                               Read the value of                                                              the register                                   22  write.sub.-- value(NumericType)+                                                                Boolean Type                                                                              Write the value of                                                             the register                                   ______________________________________                                    

                                      TABLE 6                                      __________________________________________________________________________     NumericBoundedRegister (NBR) - class = 23                                      This defines a numeric value bounded by two values.                            #  Method         Return-type                                                                           Descripiton                                           __________________________________________________________________________     20 read.sub.-- time( )*                                                                          TimeType                                                                              Read the time of last update                          21 read.sub.-- value( )*                                                                         NumericType                                                                           Read the value of the register                        22 write.sub.-- value(NumericType)*                                                              BooleanType                                                                           Write the value of the register. If the value                                  is                                                                             outside the prescribed bounds, no value will be                                written and an excepeition will be returned.          540                                                                               read.sub.-- bounds( )                                                                         NumeriArray                                                                           Read the bounds of the register. The numeric                            Type   array will have two elements.                         541                                                                               write.sub.-- bounds(NumericArrayType)                                                         BooleanType                                                                           Write the bounds of the register. The first                                    array element will be the low bound and the                                    second will be the hight bound.                       __________________________________________________________________________

                  TABLE 7                                                          ______________________________________                                         NumericVariableRegister (NVR) - class = 25                                     This defines a numeric storage location.                                       #   Method           Return-type                                                                               Description                                    ______________________________________                                         20  read.sub.-- time( )*                                                                            TimeType   Read the time of the                                                           last update                                    21  read.sub.-- value( )*                                                                           NumericType                                                                               Read the value of                                                              the register                                   22  write.sub.-- value(NumericType)*                                                                BooleanType                                                                               Write the value of                                                             the register                                   ______________________________________                                    

                  TABLE 8                                                          ______________________________________                                         DeltaRegister (DR) - class = 26                                                This defines a delta-function value.                                           #   Method          Return-type Description                                    ______________________________________                                         20  read.sub.-- time( )*                                                                           TimeType    Read the time of                                                               last update                                    21  read.sub.-- value( )+                                                                          VoidType    Read the delta value                           22  write.sub.-- value(VoidType)*                                                                  Boolean Type                                                                               Output a delta-pulse                           ______________________________________                                    

                                      TABLE 9                                      __________________________________________________________________________     Arrayregister (AR) - class = 27                                                This is the parent class for all registers containing arrays.                  # Method          Return-type                                                                           Description                                           __________________________________________________________________________     20                                                                               read.sub.-- time( )*                                                                           TimeType                                                                              Read the time of last update                          21                                                                               read.sub.-- value(RangeType)+                                                                  VoidType                                                                              Read a range of values.                               22                                                                               write.sub.-- value(IndexType, VoidType)+                                                       BooleanType                                                                           Write values at index                                 35                                                                               read.sub.-- depth( )                                                                           SizeType                                                                              Read the depthe of the array                          36                                                                               write.sub.-- depth(SizeType)                                                                   BooleanType                                                                           Write the depth of the array                          37                                                                               read.sub.-- rollover( )                                                                        UnsignedType                                                                          Read rollover value - value is the                                             highest count that can be reached                                              before rollover to 0.                                 __________________________________________________________________________

                  TABLE 10                                                         ______________________________________                                         BooleanArrayRegister (BAR) - class = 28                                        This class defines a non-circular array of Boolean values.                     #   Method         Return-type Description                                     ______________________________________                                         20  read.sub.-- time( )*                                                                          TimeType    Read the time of last                                                          update                                          21  read.sub.-- value(RangeType)+                                                                 BooleanArray                                                                               Read a range of values.                                            Type                                                        22  write.sub.-- value(IndexType,                                                                 BooleanType Write values at index                               BooleanArrayType)+                                                         35  read.sub.-- depth( )*                                                                         SizeType    Read the depth of                                                              the array                                       36  write.sub.-- depth(SizeType)*                                                                 BooleanType Write the depth of                                                             the array                                       37  read.sub.-- rollover( )*                                                                      UnsignedType                                                                               Read rollover value.                            ______________________________________                                    

                  TABLE 11                                                         ______________________________________                                         NumericArrayRegister (NAR) - class = 29                                        This class defines a non-circular array of numeric values.                     #   Method          Return-type                                                                               Description                                     ______________________________________                                         20  read.sub.-- time( )*                                                                           TimeType   Read the time of                                                               last update                                     21  read.sub.-- value(RangeType)+                                                                  NumericArray                                                                              Read a range of                                                     Type       values.                                         22  write.sub.-- value(IndexType,                                                                  BooleanType                                                                               Write values at index                               NumericArrayType)+                                                         35  read.sub.-- depth( )*                                                                          SizeType   Read the depth of the                                                          array                                           36  write.sub.-- depth(SizeType)*                                                                  BooleanType                                                                               Write the depth of                                                             the array                                       37  read.sub.-- rollover( )*                                                                       UnsignedType                                                                              Read rollover value.                            ______________________________________                                    

                                      TABLE 12                                     __________________________________________________________________________     LogRegister (LR) - class = 30                                                  This class defines a circular array of log-type                                structures. This class is intended for the                                     implenemtation of any kind of historic log.                                    # Method      Return-type                                                                           Description                                               __________________________________________________________________________     20                                                                               read.sub.-- time( )*                                                                       TimeType                                                                              Read the time of last update                              21                                                                               read.sub.-- value(RangeType)+                                                              LogArrayType                                                                          Read a range of records.                                  22                                                                               write.sub.-- value(IndexType,                                                              BooleanType                                                                           Write the records at index                                  LogArrayType)+                                                               35                                                                               read.sub.-- depth( )+                                                                      BooleanType                                                                           NotSupported                                              36                                                                               write.sub.-- depth( )+                                                                     BooleanType                                                                           NotSupported                                              37                                                                               read.sub.-- rollover( )*                                                                   UnsignedType                                                                          Read rollover value.                                      40                                                                               read.sub.-- position( )                                                                    IndexType                                                                             Read the present position. Note: Upon leaving                                  the factory, the position = 0 (i.e. the first                                  record will be written into position 0). The                                   position always indicates where the next record                                will be written.                                          41                                                                               write.sub.-- position(IndexType)                                                           BooleanType                                                                           Write the present position                                __________________________________________________________________________

                                      TABLE 13                                     __________________________________________________________________________     EventLogRegister (ELR) - class = 31                                            This class defines a circular array of event structures                        and a non-circular array of alarms. It is derived from                         the LogRegister class. The following methods are supported.                    #  Method        Return-type                                                                            Description                                           __________________________________________________________________________     20 read.sub.-- time( )*                                                                         TimeType                                                                               Read the time of the last update                      21 read.sub.-- value(RangeType)*                                                                LogArrayType                                                                           Read range of events                                  22 write.sub.-- value(IndexType,                                                                BooleanType                                                                            Write range of events                                    LogArrayType)*                                                              35 read.sub.-- depth( )+                                                                        BooleanType                                                                            NotSupported                                          36 write.sub.-- depth( )+                                                                       BooleanType                                                                            NotSupported                                          37 read.sub.-- rollover( )*                                                                     UnsignedType                                                                           Read rollover value.                                  40 read.sub.-- position( )*                                                                     IndexType                                                                              Read the present position.                            41 write.sub.-- position(IndexType)*                                                            BooleanType                                                                            Write the present position                            45 read.sub.-- alarms( )                                                                        AlarmArrayType                                                                         Read entire alarm array.                              46 write.sub.-- alarms(AlarmArrayType)                                                          BooleanType                                                                            Write entire alarm array.                             560                                                                               read.sub.-- alarm.sub.-- count.sub.-- rollover( )                                            UnsignedType                                                                           Read rollover value of alarm counters                                          in the AlarmArray - value is the                                               highest count that can be reached                                              before rollover to 0.                                 __________________________________________________________________________

                  TABLE 14                                                         ______________________________________                                         SchemaRegister (DSR) - class = 39                                              This is derived from TableRegister. A SchemaRegister                           loosely represents of a database schema, a collection                          of related database tables. In the current embodiment,                         the tables are not accessible via methods. These                               registers are used primarily as inputs to specialized                          modules that allow indirect access to the tables.                              #   Method      Return-type                                                                               Description                                         ______________________________________                                         20  read.sub.-- time( )*                                                                       TimeType   Read the time of the last update.                   21  read.sub.-- value( )+                                                                      BooleanType                                                                               NotSupported.                                       22  write.sub.-- value( )+                                                                     BooleanType                                                                               NotSupported.                                       ______________________________________                                    

                                      TABLE 15                                     __________________________________________________________________________     Log View Register (LVR) - class = 40                                           The Log View Register class is derived from Register.                          In database terminology, a view is a database table                            that is derived from queries on other database tables.                         Here a "view" is extended to mean a specialized                                representation of table or group of tables. A log View                         Register is used to access data stored in the Table                            Registers associated with the creator module (see Log                          View Module). Data retrieved from the tables is re-                            formatted and returened as Composite Log Records.                              #  Method        Return-type                                                                             Description                                          __________________________________________________________________________     20 read.sub.-- time( )*                                                                         TimeType Read the time of the last update.                    21 read.sub.-- value( SearchCriteria )+.                                                        CompositeLogArray                                                                       Returns all records that match                                                 SearchCriteria.                                      22 write.sub.-- value( )+                                                                       BooleanType                                                                             Not supported.                                       583                                                                               read.sub.-- updates( SearchCriteria )                                                        CompositeLogArray                                                                       The first time this method is invoked (for a                                   particular program), all records that match                                    the SearchCriteria are returned.                                               Subsequently, only the newest matching                                         records are returned.                                __________________________________________________________________________

                                      TABLE 16                                     __________________________________________________________________________     EventViewRegister (EVR) - class = 41                                           The EventViewRegister class is a LogViewRegister that                          specializes the in storage of CompositeEventRecords.                           It also allows these records to be marked as                                   acknowledged and sends prioritized alarm messages to                           registered clients.                                                            #  Method         Return-type                                                                              Description                                        __________________________________________________________________________     20 read.sub.-- time( )*                                                                          TimeType  Read the time of the last update.                  21 read.sub.-- value( SearchCriteria )+                                                          CompositeEventArray                                                                      Returns all records that match                                                 SearchCriteria.                                    22 write.sub.-- value( )*                                                                        BooleanType                                                                              Not supported.                                     583                                                                               read.sub.-- updates( SearchCriteria )+                                                        CompositeEventArray                                                                      See LogViewRegister                                584                                                                               acknowledge(UnsignedArrayType)                                                                Boolean Type                                                                             Marks the specified event records as                                           acknowledged. The argument is an array of                                      recordIDs.                                         __________________________________________________________________________

                                      TABLE 17                                     __________________________________________________________________________     WaveformRegister (WR) - class = 32                                             This class defines an array of points defining a waveform.                     # Method        Return-type                                                                           Descripiton                                             __________________________________________________________________________     20                                                                               read.sub.-- time( )*                                                                         TimeType                                                                              Read the time of last update                            21                                                                               read.sub.-- value( )+                                                                        WaveformType                                                                          Read the present value of the register                  22                                                                               write.sub.-- value(WaveformType)+                                                            BooleanType                                                                           Write the present value of the register                 __________________________________________________________________________

                                      TABLE 18                                     __________________________________________________________________________     EventRegister (ER) - class = 33                                                This class defines a register which holds an evet.                             # Method       Return-type                                                                            Description                                             __________________________________________________________________________     20                                                                               read.sub.-- time( )*                                                                        TimeType                                                                               Read the time of last update                            21                                                                               read.sub.-- value( )+                                                                       EventType                                                                              Read the present value of the register                  22                                                                               write.sub.-- value(EventType)+                                                              BooleanType                                                                            Write the present value of the register                 __________________________________________________________________________

                                      TABLE 19                                     __________________________________________________________________________     TimeRegister (TR) - class = 34                                                 This class defines a register which holds unformatted time.                    # Method      Return-type                                                                            Description                                              __________________________________________________________________________     20                                                                               read.sub.-- time( )*                                                                       TimeType                                                                               Read the time of last update                             21                                                                               read.sub.-- value( )+                                                                      TimeType                                                                               Read the present value of the register                   22                                                                               write.sub.-- value(TimeType)+                                                              Boolean Type                                                                           Write the present value of the register                  __________________________________________________________________________

It is also contemplated that a TableRegisterClass will be defined. The TableRegisterClass represents a database table, rows of data organized into distinct columns. It is presently envisioned that the database tables will not be accessible using methods. These registers may be used permanently as inputs to specialized modules that allow indirect access to the tables.

Registers operate only as servers in the architecture. In other words they only respond to method invocations. Some of the most commonly used registers in the preferred embodiment are boolean registers, enumerated registers, numeric registers and numeric bounded registers. A flow chart for the server operation of a boolean register is shown in FIGS. 20A-20C. A flow chart for the server operation of an enumerated register is shown in FIGS. 21A-21B. A flow chart for the server operation of a numeric register is shown in FIGS. 22A-22B. A flow chart for the server operation of a numeric bounded register is shown in FIGS. 23A-23B.

It will be recognized by those skilled in the art that the registers' functionality can be embedded within the modules.

The modules provide the IED the functionality in the architecture. FIG. 11 schematically illustrates a preferred embodiment of the properties of the modules. The modules can be considered as "black boxes" that read data at the inputs, manipulate the data in some fashion, and write the result to outputs. Input data is read from registers and output data is written to registers. For all types of modules, the links to input registers can be programmed, but the links to output registers are fixed. Most modules have links to registers which contain setup information--these links are also fixed, and the module can only read them. FIG. 12 illustrates the data flow for a module. A module 61 is linked to input registers 63a-63n through programmable links 69a-69n. Setup registers 67a-67n are linked to module 61 through links 72a-72n which are not programmable. Output registers 64a-64n are linked to module 61 through links 70a-70n which also are not programmable.

In the preferred embodiment, the modules have the following properties

An array of handles (input handles) point to the input registers. The module has shared ownership of these registers. The module reads a register using the Read₋₋ Value method.

Module setup data (such as scaling information) is stored in registers. An array of handles (setup handles) point to these Registers. There is one exception: For a manager module these Handles point to other modules rather than registers. The module has shared ownership of these objects.

The module uses the input data and setup data to produce output data according to the function of the module which is described by the module behavior.

An array of handles (output handles) point to the output registers. The module has shared ownership of these registers. A module writes these registers using the Write₋₋ Value method.

UpdatePeriod contains the period at which the module updates the output registers.

ModuleSecurity contains the security level which the module uses when invoking methods on other objects.

The module has a class which is unique to that type of module. (e.g. All setpoint modules would have the same class).

The module has a name. This name is fixed (read only) and is different in every module.

The module has a label which can be programmed.

A method security level is defined for every method which can be invoked on a module. Thus, there is a security parameter for every method which can be invoked on the module.

The module has owners which are listed in an array of Handles. This array lists all the module(s) that have shared ownership of the module.

A module is created by a manager using the Create₋₋ Module() method. When the module is created all output registers and setup registers are also created. However, input registers are not created when a module is created. Often, a manager will have a fixed number of modules and the Create₋₋ Module() method will not be supported.

The module class (class=500) is derived from the base class. The methods listed below in Table 20 are common to all module classes (all module classes are inherited from this module class).

                                      TABLE 20                                     __________________________________________________________________________     #  Method            Return-type                                                                           Description                                        __________________________________________________________________________     1000                                                                              read.sub.-- input.sub.-- handles( )                                                              HandleArray                                                                           Returns a list of the handles to the                                           registers                                                               Type   that are connected as inputs to the manager                                    or module. (In the current embodiment,                                         managers do not have inputs.)                      1001                                                                              write.sub.-- input.sub.-- handles(HandleArrayType)                                               BooleanType                                                                           Accepts a list of handles and attempts to                                      link                                                                           a module or manager to these input                                             registers.                                                                     (In the current embodiment, managers do not                                    have inputs.) The handle order is defined in                                   the module definitions. If one of the                                          handles                                                                        is incorrect the method will fail and NO                                       handles will be written (i.e. all or                                           nothing).                                          1002                                                                              read.sub.-- input.sub.-- classes( )                                                              ArrayUnsigned                                                                         Reads the allowed register classes for the                              ArrayType                                                                             write.sub.-- input.sub.-- handles method. The                                  returned                                                                       array has the same number of elements as                                       the HandleArray used in the                                                    write.sub.-- input.sub.-- handles method. If                                   the returned                                                                   array has an element that contains a Null                                      rather than a class this indicates that this                                   input element cannot be programmed.                1003                                                                              read.sub.-- output.sub.-- handles( )                                                             HandleArray                                                                           Returns a list of handles to the output                                 Type   registers of a module or manager. (In the                                      current embodiment, managers do not have                                       outputs.) The handle order is defined in the                                   module definitions.                                1004                                                                              read.sub.-- setup.sub.-- handles( )                                                              HandleArray                                                                           Returns a list of handles to the setup                                         register                                                                Type   of a module or a list of handles to modules                                    for a manager. The handle order is defined                                     in                                                                             the module definitions.                            80 read.sub.-- setup.sub.-- counter( )                                                              CounterType                                                                           Returns a number indicating how many times                                     the module or manager has had its                                              configuration changed. A master device can                                     keep a local copy of this number. If another                                   master device changes the setup of the slave                                   device, the first manager can detect the                                       change by comparing its count with the                                         current count.                                     81 read.sub.-- update.sub.-- counter( )                                                             CounterType                                                                           Returns a number indicating how many times                                     the module or manager has successfully                                         invoked a method to write a new value to its                                   output registers. A master device can then                                     determine if it is necessary to read the                                       output                                                                         from the module or manager. (In the current                                    embodiment, managers have no outputs.)             1005                                                                              read.sub.-- update.sub.-- period( )                                                              StringType                                                                            Returns a number indicating the minimum                                        amount of time there will between the module                                   or manager updating its output registers.                                      (In                                                                            the current embodiment, managers have no                                       outputs.)                                                                      Typical response is one of:                                                    "one cycle"                                                                    "one second"                                                                   "two cycles"                                       1006                                                                              read.sub.-- module.sub.-- security( )                                                            SecurityType                                                                          Returns a numbers indicating the security                                      access a module has. Other modules or                                          registers may refuse to execute a method                                       invoked by a module which does not have a                                      high enough security level.                        __________________________________________________________________________

Table 21 below lists the behavior details for the module parameters.

                  TABLE 21                                                         ______________________________________                                         Module Parameter                                                                          Behavior                                                            ______________________________________                                         update.sub.-- counter                                                                     will be incremented every time a write.sub.-- value( )                         method is successfully invoked on one of the                                   registers identified by the output handles.                                    Note: by default the update counter will be incre-                             mented every time an module writes an event                                    register.                                                           setup.sub.-- counter                                                                      will be incremented every time a write.sub.-- value( )                         method is successfully invoked on one of the sys-                              tem registers identified by the setup handles and                              every time the write.sub.-- input.sub.-- handles( )                            method is successfully invoked.                                     ______________________________________                                    

Table 22 below provides a list of the modules (including the corresponding input, output and setup registers) presently supported by the presently preferred embodiment.

                                      TABLE 22                                     __________________________________________________________________________     #  Module Name                                                                            Input Registers                                                                          Output Registers                                                                          Setup Registers                                                                         Module Description                    __________________________________________________________________________     501                                                                               Power Meter                                                                            V1(NAR)   Vabc*(NVR).sup.1                                                                          ode(ENR) Basic 3-phase power met                          V2(NAR)   Vllabc*(NVR)                                                                              PT Pri Volts(NBR)                                                                       met meter.                                       V3(NAR)   labc*(NVR) PT Sec Volts(NBR)                                                                       PhaseOrder:                                      l1(NAR)   KWabc*(NVR)                                                                               CT Pri (NMR)                                                                            "ABC"                                            l2(NAR)   KVARabc*(NVR)                                                                             CT Sec l(NBR)                                                                           "ACB"                                            l3(NAR)   KVAabe*(NVR)                                                                              14 CT Pri l(NBR)                                                                        NormFreq:                                        l4(NAR)   PFSIGNabc*(NVR)                                                                           14 CT Sec l(NBR)                                                                        "50"                                                       PFLEADabc*(NVR)                                                                           l1 Polarity(ENR)                                                                        "60"                                                       PFLAGabc*)NVR)                                                                            l2 Polarity(ENR)                                                                        "400"                                                      Vunbal(NVR)                                                                               l3 Polarity(ENR)                                                                        PhaseLabels:                                               lunbal(NVR)                                                                               PhaseOrder(ENR)                                                                         "ABC"                                                      l4(NVR)    NormFreq(ENR)                                                                           "RST"                                                      Iresidual(NVR)                                                                            PhaseLabels                                                                             "XYZ"                                                      PhaseRev(BVR)                                                                             (ENR)    "RYB"                                                      LineFreq(NVR)                                                                  Event(ER)                                                 502                                                                               Analog Input      ScaledAnalog(NVR)                                                                         Zero Scale(NBR)                                                                         Analog Input function.                                     Event(ER)  Full Scale(NBR)                                                                         Port indicates H/W input                                              Port(ENR)                                                                               port.                                 503                                                                               Analog Output                                                                          Source(NVR)                                                                              State(NVR) Zero Scale(NBR)                                                                         Analog Output function.                                    Event(ER)  Full Scale(NBR)                                                                         OutputState gives present                                             OutputMode                                                                              output value as a % of                                                (ENR)    output full scale.                                                    Port(ENR)                                                                               OutputMode:                                                                    "0-20ma"                                                                       "4-20ma"                                                                       note: OutputMode is not                                                        supported for all devices.                                                     Port indicates H/W output                                                      port.                                 504                                                                               Digital Input     State(BVR) InputMode (ENR)                                                                         Processes raw digital                                      Trigger(DR)                                                                               EvLogMode                                                                               signals received from H/W                                  Event(ER)  (ENR)    digital input channel.                                                InPolarity(ENR)                                                                         Trigger on valid state                                                Debounce(NBR)                                                                           changes.                                                              Port(ENR)                                                                               InputMode:                                                                     "Pulse"                                                                        "KYZ"                                                                          EvLogMode:                                                                     "Log Off"                                                                      "Log On"                                                                       InPolarity:                                                                    "non-inverting"                                                                "inverting"                                                                    Debounce in ms.                                                                Port indicates H/W input                                                       port.                                 505                                                                               Digital Output                                                                         Source(BVR)                                                                              State(BVR) EvLogMode                                                                               Provides raw bit pattern                         ForceOn(DR)                                                                              Mode(BVR)  (ENR)    for H/W digital output                           ForceOff(DR)                                                                             Event(ER)  OutPolarity(ENR)                                                                        channel.                                         Normal(DR)           PulseWidth(NBR)                                                                         EvLogMode:                                                            Port(ENR)                                                                               "Log Off"                                                                      "Log On"                                                                       OutPolarity:                                                                   "non-inverting"                                                                "inverting"                                                                    PulseWidth:                                                                    0 = continuous output.                                                         not 0 = pulse width in                                                         ms.                                                                            Port indicates H/W output                                                      port.                                 506                                                                               Pulser  Source(DR)                                                                               Event(ER)  PulseWidth(NBR)                                                                         Proves pulse output (e.g.                                             OutputMode                                                                              for Kwh pulsing). Output                                              (ENR)    Port is pulsed every time                                             OutPolarity(ENR)                                                                        a pulse is received at the                                            Port(ENR)                                                                               Source input.                                                                  PulseWidth specified in                                                        ms.                                                                            OutputMode:                                                                    "Pulse"                                                                        "KYZ"                                                                          OutPolarity:                                                                   "non-inverting"                                                                "inverting"                                                                    Port indicates H/W output                                                      port.                                 508                                                                               SWD     Source(NVR)                                                                              SWD(NVR)   Period(NBR)                                                                             Provides SWD on source                           Sync(DR)  Prediction(NVR)                                                                           #Periods(NBR)                                                                           input.                                           Reset(DR) Event(ER)  SyncMode(ENR)                                                                           Period in minutes.                                                    PredictSpeed                                                                            SyncMode:                                                             (NBR)    "internal"                                                                     "external"                                                                     Sync input is used in                                                          external sync mode,                                                            otherwise un-used.                                                             PredictSpeed from 0-99                                                         (99 = fast response).                 509                                                                               TD      Source(NVR)                                                                              TD(NVR)    Period(NBR)                                                                             Provides Thermal Demand                          Reset(DR) Event(ER)  TimeConstant                                                                            calculation on a single                                               (NBR)    source input.                                                                  Period in minutes.                                                             TimeConstant is a                                                              percentage of the Period.             510                                                                               Integrator                                                                             Integrand(NVR)                                                                           Result(NVR)                                                                               Divisor(NBR)                                                                            Provides integration                             Enable(BVR)                                                                              Pulse(DR)  IntMode(ENR)                                                                            function.                                        Reset(DR) Event(ER)  PulseSize(NBR)                                                                          Enable allows gating                                                           Divisor in seconds (for                                                        Kwh the Divisor would be                                                       3600)                                                                          IntMode:                                                                       "forward"                                                                      "reverse"                                                                      "absolute"                                                                     "net"                                                                          The Pulse output will be                                                       pulsed when the Result                                                         output changes by the                                                          amount specified in                                                            PulseSize setup . . .                 511                                                                               Min     Source(NVR)                                                                              Min(NVR)            Scans Source register for                        Enable(BVR)                                                                              Trigger(DR) Event(ER)                                                                              new minimum values.                              Reset(DR)                     Enable allows gating for                                                       every new minimum the                                                          Min and Trigger registers                                                      are updated.                          512                                                                               Max     Source(NVR)                                                                              Max(NVR)            Scans Source register for                        Enable(BVR)                                                                              Trigger(DR) Event(ER)                                                                              new maximum values.                              Reset(DR)                     Enable allows gating for                                                       every new maximum the                                                          Max and Trigger registers                                                      are updated.                          513                                                                               Setpoint                                                                               Source(NVR/BVR)                                                                          Status(BVR)                                                                               HiLim(NBR)                                                                              Provides hysteric                                Enable(BVR)                                                                              Trigger(DR)                                                                               LoLim(NBR)                                                                              setpoint function on                             Reset(DR) Event(ER)  TDOperate(NBR)                                                                          numberic of loolean value.                                            TDRelease(NBR)                                                                          Enable allows gating.                                                 InputMode(ENR)                                                                          Trigger on setpoint going                                             EvaluateMode                                                                            ACTIVE.                                                               (ENR)    TDOperate and TDRelease                                               EventPri(NBR)                                                                           in ms.                                                                         InputMode:                                                                     "Signed"                                                                       "Absolute"                                                                     EvaluateMode:                                                                  "GreaterThan"                                                                  "LessThan"                            514                                                                               FFT     Source(NAR)                                                                              FFT(NAR)            Performs FFT calculations                        Enable(BVR)                                                                              Event(ER)           on input source array and                                                      generates an array of                                                          complex numbers.                      515                                                                               Harmonics                                                                              Source(NAR)                                                                              HD1(NVR)            Performs harmonics                       Analyzer                                                                               Enable(BVR)                                                                              . . . HDN(NVR)      calculations on an N-size                                  THD(NVR)            array of complex numbers                                   TEHD(NVR)           (i.e. from an FFT module).                                 TOHD(NVR)                                                                      KFactor(NVR)                                                                   Event(ER)                                                 516                                                                               Recorder                                                                               Source1   RecLog(LR) Depth(NBR)                                                                              Provides a snapshot of the                       (NVR/BVR/NAR/                                                                            Event(ER)  RecMode(ENR)                                                                            input source registers                           BAR/WR)              EvLogMode                                                                               when trigger register is                         . . . SourceN        (ENR)    pulsed. Can record                                                             waveforms, arrays, and                           (NVR/BVR/NAR/                 single value registers.                          BAR/WR)                       Enable allows gating                             Enable(BVR)                   RecMode:                                         Trigger(DR)                   "Circular"                                                                     "Stop-when-full"                                                               EvLogMode:                                                                     "Log Off"                                                                      "Log On".                             517                                                                               Waveform                                                                               RawWF(NAR/BAR)                                                                           FormattedWF(WR)                                                                           Format(ENR)                                                                             Formats waveform data.                   Formatter         Event(ER)           Format (#sampls/cyc x                                                          #cycles)                                                                       "128×12"                                                                 "64×28"                                                                  etc . . .                             518                                                                               Periodic                                                                               Enable(BVR)                                                                              Trigger(DR)                                                                               Period(NBR)                                                                             Pulses the Trigger output                Timer   Initialize(DR)                                                                           Event(ER)  TimingMode                                                                              whenever the timer value                                              (ENR)    reaches zero.                                                         ResetMode(ENR)                                                                          Period in ms.                                                                  TimingMode:                                                                    "Sync to UNIX"                                                                 "Sync to Init"                                                                 ResetMode:                                                                     "init to Period"                                                               "init to zero"                        519                                                                               One-shot                                                                               Enable(BVR)                                                                              State(BVR) Period(NBR)                                                                             Provides a one-shot timer.               Timer   TriggerIn(DR)                                                                            TriggerOut(DR)      State:                                                     Event(ER)           1 when timer is running                                                        0 after time out                                                               The Trigger Out activates                                                      at the end of the timing                                                       interval.                                                                      Period in ms.                         520                                                                               Counter Trigger(DR)                                                                              Count(NVR) Multiplier(NBR)                                                                         Increment/Decrement                              Initialize(DR)                                                                           Event(ER)  UpDown(ENR)                                                                             Count register by the                                                          amount specified in the                                                        Multiplier register each                                                       time the counter is                                                            triggered.                                                                     UpDown:                                                                        "Count Down"                                                                   "Count Up"                            521                                                                               LogicalAndOr                                                                           Source1(BVR)                                                                             Results(BVR)                                                                              Mode(ENR)                                                                               Performs either Logical                          . . . SourceN(BVR)                                                                       Event(ER)  EvLogMode                                                                               AND, NAND or function on                                              (ENR)    the source inputs.                                                             Mode:                                                                          "AND"                                                                          "NAND"                                                                         "OR"                                                                           EvLogMode:                                                                     "Log Off"                                                                      "Log On"                              522                                                                               Event Log                                                                              Event1(ER)                                                                               EventLog(ELR)                                                                             EvLogDepth                                                                              Logs all event records in                Controller                                                                             . . . EventN(ER)     (NBR)    EventLog regardless of                                                AlarmPriority                                                                           priority.                                                             (NBR)    Keeps track of previous                                                        and presently active                                                           alarms in EventLog. Any                                                        event with a priority equal                                                    to or above AlarmPriority                                                      is an alarm.                          528                                                                               LogSchema                                                                              LogInout1 (LR)                                                                           LogSchema(DSR)      Uploads log records from                         . . . LogInputN (LR)          the remote LogRegister                                                         inputs and stores them in                                                      a database schema.                    529                                                                               EventSchema                                                                            EventInput1 (ELR)                                                                        EventSchema(DSR)    Combines event records                           . . . EventInputN (ELR)       and alarm information                                                          from each IED and stores                                                       the data in a database                                                         schema.                               532                                                                               Label   EventLog1 (ELR)                                                                          LableTable (DTR)    Maintains a historic list of                     . . . EventLogN (ELR)         all labels that exist on                                                       each IED. The remote                                                           EventLogRegister inputs                                                        can be used to track label                                                     changes. Initially all labels                                                  are read by accessing the                                                      feature manager.                      533                                                                               LogView LogSchema (DSR)                                                                          LogView (LVR)       Acts as a bridge between                         LabelTable (DTR)              the input database tables                                                      and the output                                                                 LogViewRegister. The                                                           input tables are joined to                                                     produce detaild log                                                            records.                              534                                                                               EventView                                                                              EventSchema (DSR)                                                                        EventView (EVR)     Acts as a bridge between                         LabelTable (DTR)              the input database tables                                                      and the output                                                                 EventViewRegister. The                                                         input tables are combined                                                      to produce detailed event                                                      records.                              524                                                                               Comm    Reset(DR) Event(ER)  CommMode Communications Interface.                                             (ENR)                                                                          Baudrate(ENR)                                                                           CommMode:                                                             HandshakeMode                                                                           "RS232"                                                               (ENR)    "RS485"                                                               RTSLevel(ENR)                                                                           BaudRate:                                                             CTSLevel(ENR)                                                                           "300"                                                                 RTSDelay(NBR)                                                                           "1200"                                                                UnitD(NBR)                                                                              etc . . .                                                                      HandshakeMode:                                                                 "RTS with level"                                                               "CTS with level"                                                               RTSLevel:                                                                      "active low"                                                                   "active high"                                                                  CTSLevel:                                                                      "active low"                                                                   "active high"                                                                  RTSDelay:                                                                      specifies transmission                                                         delay time (in ms) after                                                       RTS has been raised.                  523                                                                               Data Acquisition  Output1(NAR)        Provides sampled data                                      . . . OutputN(NAR)  from the waveforms of a                                                        power system.                         530                                                                               External Control  Numeric1(NVR)       Provides registers that can                                . . . NumericN(NVR) be controlled externally.                                  Trigger1(DR)                                                                   . . . TriggerN(DR)                                                             Switch1(BVR)                                                                   . . . SwitchN(BVR)                                        525                                                                               Diagnostics                                                                            Reset(DR) Output1(BVR/NVR)    Output registers provide                                   . . . OutputN(BVR/NVR)                                                                             diagnostic features . . .                                  Event(ER)                                                 526                                                                               Real-time Clock   Time(TR)            Provides real-time clock                                                       facility.                                                                      Time register in universal                                                     (GMT) seconds.                        527                                                                               Factory           Event(ER)  Setup1   Used for Factory                                                      (ENR/NBR)                                                                               Purposes.                                                             . . . SetupN                                                                            All other uses violate the                                            (ENR/NBR)                                                                               architecture.                                                                  It has no owner and                                                            cannot be created or                                                           dewtroyed ("it merely                                                          exists").                                                                      It can be accessed only                                                        with the factory security                                                      level.                                531                                                                               Symmetrical                                                                            Source1(NAR)                                                                             ZeroSeqMag(NVR)                                                                           Harmonic(NBR)                                                                           Calculates the magnitude                 Components                                                                             Source2(NAR)                                                                             ZeroSeqPhase(NVR)   and phase for each                               Source3(NAR)                                                                             PosSeqMag(NVR)      sequence component for a                         Enable(BVR)                                                                              PosSeqPhase(NVR)    particular harmonic.                                       NegSeqMag(NVR)      Typically, FFT Modules is                                  NeqSeqPhase(NVR)    used to produce the                                        Event(ER)           Numeric Array Registers                                                        inputs.                               __________________________________________________________________________      .sup.1 The method read.sub.-- output.sub.-- handles() will return handle       in the order given here. This also applied to the methods read.sub.--          input.sub.-- handles and read.sub.-- setup.sub.-- handles() for all            modules defined in this document.                                              Legned of register acronyms:                                                   BAR -- Boolean Array Register                                                  BVR -- Boolean Variable Register                                               CR -- Counter Register                                                         DR -- Delta Register                                                           ELR -- Event Log Register                                                      ENR -- Enumerated Register                                                     ESR -- Event Schema Register                                                   EVR -- Event Register                                                          LR -- Log Register                                                             LSR -- Log Schema Register                                                     NAR -- Numeric Array Register                                                  NBR -- Numeric Bounded Register                                          

In the following description reference is made to "managers". It will be noted that managers are just a specific type of module which have additional functionality. The purpose of the managers is to manage modules. One manager is needed for each practical group of modules, such as setpoint modules and min modules.

Table 23 below provides a list of the methods which are added specifically for the manager class. (All class and module class methods are inherited by the manager class but are not shown here for reasons of brevity.)

                                      TABLE 23                                     __________________________________________________________________________     #  Method         Return-type                                                                          Description                                            __________________________________________________________________________     100                                                                               read.sub.-- module.sub.-- setups.sub.-- counter( )                                            CounterType                                                                          Returns a number indicating how many times                                     the setup registers of the modules below a                                     manager have been changed. The master                                          device can keep a local count of this number                                   in order to determine if another master device                                 has successfully invoked a method to change                                    the setup of the device. For instance, if a                                    master device keeps this count for the feature                                 manager, it can tell if any setup register on                                  the deivce has been changed without going to                                   each individual module.                                101                                                                               read.sub.-- module.sub.-- updates.sub.-- counter( )                                           CounterType                                                                          Returns a number indicating how many times                                     the output registers of the modules and                                        managers beneath a certain manager have                                        been updated. Used in the same fashion as                                      Read Module Setups Counter, the Read                                           Module Updates Counter is used to determine                                    if any of the modules beneath the manager                                      have successfully invoked a method to update                                   their output registers. (In the current                                        embodiment, managers have no outputs.)                 1500                                                                              create.sub.-- module(Class Type)                                                              HandleType                                                                           Creates a module and stores the module                                         handle in the setup handles array; return                                      handle to module. The method                                                   read.sub.-- managed.sub.-- class indicates which                               class of                                                                       module can be created.                                 1501                                                                              destroy.sub.-- module(HandleType)                                                             BooleanType                                                                          Destroys a module. Handle must be one of                                       setup handles or an exception will be returned                                 and the method will fail. The resources for                                    that module are then available to perform                                      other functions on the device.                         1502                                                                              read.sub.-- managed.sub.-- class( )                                                           ClassType                                                                            Returns the class of module which can be                                       created with the create.sub.-- module                  __________________________________________________________________________                             method.                                           

Every system has a "root" manager module called the feature manager. The feature manager has setup handles to all the other managers. Importantly, the feature manager handle is identical for all systems. The handle for the feature manager is 2. Starting with this handle, it is possible to determine the entire system configuration.

As was mentioned previously, modules act as both clients and servers in the object oriented architecture. In the present embodiment, the client and server portion of the modules operate separately. The server portion of the modules respond to method invocations. The server portion follows the same logic for all modules (except the managers) on the device. A flow chart of the logic for the server portion of a module is shown in FIGS. 12a-12c.

A description is now given of how the modules described above are used in the system of FIGS. 1-3. In the preferred embodiment the output registers from the data acquisition module 152 (FIG. 4) (which are digital signals representing the samples of the voltage and current) are permanently connected as input registers 120 of a module called the power meter module 126 (FIG. 5). Conceptually, the data acquisition module encompasses signal conditioning circuitry 60, 62, 64, 66A, 66B, 66C, 68A, 68B, 68C, 70, the A/D converters 29, 30 and software in the DSP 28. The interface between the data acquisition module and the power meter module includes the dual port RAM 27. A flow chart for the logic of the client portion of the data acquisition module 152 is shown in FIG. 4A. The power meter module 126 owns setup registers 122 which modify the operation of the power meter module 126 and output registers 124 which contain the results of the calculations that the power meter module does and can be connected to other modules. A flow chart of the logic for the power meter module 126 is shown in FIGS. 5A-5L.

The module called the analog input module is an example of a module which connects to a physical signal in a different way. A preferred embodiment of the analog input module 128 is illustrated schematically in FIG. 6. An exemplary embodiment of the logic for the client portion of the analog input module of FIG. 6 is illustrated in flowchart form in FIG. 6A. The analog input module 128 owns a port setup register 130 which defines which of the auxiliary input signals 20 the module is associated with. Analog input modules can also be connected to digital I/O signals 44 (FIG. 2). In this configuration, the Digital I/O transceiver 49 operates in input mode and the analog input module converts the frequency of the digital signal into a number. In this embodiment, an external voltage to frequency converter is connected to the digital input signal line.

Analog output modules can also be connected to the Digital I/O Signals 44. In this configuration, an external device is connected to the I/O line which converts the digital signals coming from the analog output module 130 to an analog signal. A preferred embodiment of the analog output module 130 is illustrated schematically in FIG. 7. An exemplary embodiment of the logic for the client portion of the analog output module 130 is illustrated in FIG. 7A in flowchart form.

The digital input module 140 transforms a digital I/O signal 44 into a form that can be used as an input to other modules. A preferred embodiment of the digital input module 140 is illustrated schematically in FIG. 8. An exemplary embodiment of the logic for the client portion of the digital input module 140 is illustrated in FIGS. 8A-8B in flowchart form.

The digital output module 150 transforms the output from another module into a signal on a digital I/O signal line 44. A preferred embodiment of the digital output module 150 is illustrated schematically in FIG. 9. An exemplary embodiment of the logic for the client portion of the digital output module 150 is illustrated in FIGS. 9A-9H in flowchart form.

Additional modules that operate only on the results of other modules are also possible. An example of one of these modules is the AND/OR module 160 illustrated schematically in FIG. 13. The AND/OR module 160 takes a number of boolean variable register inputs and performs a logical AND or OR on them to create a result. The CalcMode setup register 161 determines which AND or OR function is being executed. The EvLogMode setup register 162 determines whether events will be generated in the Event output register 163 when the Result 164 register changes. The logic for a preferred embodiment of the client portion of the AND/OR module 160 is illustrated in FIGS. 13A-13B in flowchart form. The setpoint module 172 is shown schematically in FIG. 14. The logic for a preferred embodiment of the client portion of the setpoint module 172 is shown in FIGS. 14A-14C. These modules do not interface to the outside world.

Another module of note is the EventLog module 170. The EventLog module is shown schematically in FIG. 15. A flowchart of a preferred embodiment for the client portion of the EventLog module is shown in FIG. 15A. Nearly all other modules within the device are connected to an event output register. When an unusual state arises within a module, it may send an event message to the event register. The EventLog module 170 takes event registers as an input and invokes a method to write the "event" into its event log output register. The result is that the Event Log register then contains a list of all the significant occurrences that have happened on the device. In this manner, the time as well as the effects which occur in the IED may be recorded.

An example of the events that may be generated on the power meter of the present invention can be seen in Table 24.

                                      TABLE 24                                     __________________________________________________________________________     Event #                                                                            Time     Cause Label                                                                          Cause Value                                                                            Effect Label                                                                         Effect Value                                  __________________________________________________________________________     1   Dec. 15/94 @ 800                                                                        None  External                                                                               Motor 4                                                                              Powdered Down                                 2   Dec. 15/94 @ 800                                                                        Motor 4                                                                              Powdered Down                                                                          Cooler 7                                                                             Shutdown                                      3   Dec. 15/94 @ 923                                                                        kW Phase A                                                                           1000    Over kWa                                                                             True                                          4   Dec. 15/94 @ 923                                                                        Over kWa                                                                             True    Relay 6                                                                              Closed                                        __________________________________________________________________________

In table 24 a number of events in the system are shown. Event #1 is an event that a digital input module might create if its hardware changed state. In this case, the digital input is connected to the status output of a motor. There is no cause label in this case since the cause is external to the meter. Event #2 shows an event that a digital output module might create. The source input of this digital output module is connected as the state output of the digital input module. Event #3 is an event that a setpoint module might create. The setpoint module has detected that the amount of power being consumed is too great so its status output register is set to true. This status output register is connected as the source input register to another digital output module. In Event #4 the digital output module is shown to close a relay. Therefore, the fact that kW Phase A has exceeded a certain bounds has caused an external relay to close (hopefully rectifying the problem).

A significant feature of the disclosed architecture is that the modules can be linked in arbitrary fashions to form arbitrary functional blocks comprised of networked objects.

An example application using the architecture of this invention is shown in FIG. 16. In this example, a setpoint module 172 is used to monitor Phase A current from the power meter module 126. The setpoint is enabled using a digital input module 140 which is driven by the manual switch 141. The setpoint setup registers are configured so that the setpoint goes ON when the current exceeds 100 Amps. The setpoint status output controls the digital output module 150, which drives a relay 151 which could control a motor (not shown). Whenever the phase A current exceeds 100 Amps and the manual switch 141 is closed, the relay 151 will be closed causing the motor to turn off. (Note: in this example setup registers and other registers that are not needed for the example are not shown.) It will be appreciated by those skilled in the art that the number and variety of possible additional modules and applications is unlimited.

The operation of most of the modules in the IED is governed by the client portion of the module flow controller. A flow chart for the execution of the client portion of the module flow controller is shown in FIG. 17A. The module flow controller causes different modules within the device to execute. The module flow controller only triggers modules to execute that have valid input registers. Therefore, any modules that do not meet this requirement do not use any of the processing power available to the device. The server portion of the module flow controller is executed when a module has the write input handles method invoked on it. A flow chart for the operation of the server portion of the module flow controller is shown in FIG. 17B. The server portion of the module flow controller records whether the input handles being written are valid or not. The client portion then uses this information when it makes its decision on whether to execute the module or not.

FIG. 18 schematically illustrates a preferred embodiment of a manager, the analog output manager 300. A flow chart for the logic for the server portion of a manager is shown in FIGS. 18A-18B. In the present embodiment, managers have no client portion. There is one resource manager 300 for each type of module. Each resource manager 300 may have many modules below it.

Every manager 300 in an IED resides beneath the feature manager for the device. A preferred embodiment of feature manager 400 is schematically shown in FIG. 19. A flow chart for the logic of the server portion of the feature manager is show in FIGS. 19A-19B. All the managers on the device appear as setup registers 401 to the feature manager 400. The feature manager 400 controls access to the entire device 100. Starting from the feature manager 400, a master device, such as PC 114, can determine all input, output and setup registers for every module on the IED device 100.

Each manager is said to own all the modules that appear as its setup registers. The feature manager is said to own the resource managers that appear as setup registers to it. Therefore, a hierarchy of modules exists with the feature manager on top.

In order for a master device, such as PC 114, to access the information in a slave device, such as the IED 100, it invokes methods on the managers, modules or registers. In order for a master to execute a method on a slave, it must have a handle. The handle indicates which manager, module or register the method is to be acted on. For example, the handle for the feature manager for any type of slave device is 2 in the current embodiment. This is the only thing that is fixed in the architecture and every type of device has a feature manager with a handle of 2. From this handle, the entire configuration of the device can be determined.

With the configuration of the present invention, the slave device, such as the IED's 100 may have the capability to execute many different objects, but only a limited number of objects can be executed at any one time due to processing power constraints. The flow control client controls the operation of modules. Therefore, only the modules that have valid input, output and setup registers connected to them are executed.

In order for a master device, such as a PC 114, to determine the configuration of a slave device without the master device having any previous knowledge of the configuration, the master device invokes certain methods on the feature manager. These methods are fixed in the architecture. In other words, every feature manager for every different type of slave device will interpret these methods in the same way. For instance, the master device may invoke the method Read Setup Handles on the feature manager which requests a list of the managers that reside beneath it. From this list, the master device can then go to each individual manager and request the operating modules beneath them by again executing the method Read Setup Handles. Once the master device knows which modules are operating, it can request of each module its currently connected input, output and setup registers using the appropriate methods and thus determine the entire configuration of the device. Thus, without any prior knowledge of the slave device, or its configuration, the master device can determine all characteristics of the device. The master device can then invoke other methods to change the configuration of the device. The slave devices, however can operate autonomously without the involvement of the master devices.

Thus, the slave devices, such as power monitors, can be readily configured to exactly match a user's unique requirements and to provide the ability to do so without interrupting the operation of the rest of the functions the device is performing. The slave devices, such as the IEDs, can be networked to one or more computers and the slave devices can be configured or reconfigured via the communications network.

Further, with the present invention, it is not necessary to change the software on a master device when a slave device is upgraded.

The modules are independent or autonomous. Thus, when a module is modified, there is no need to modify the other modules. As used herein the term "independent modules" means that modifications or changes can be made to one or more modules without a need to modify the remaining modules (i.e. a modification to one module has no effect on the operation or functionality of the other modules.

The feature manager keeps a count of how many times the configuration of the device has been changed. A master can invoke a the method Read Module setups counter on the feature manager to request this count. If there are multiple masters changing the configuration of the device, each master need only request this count from the feature manager to determine if the configuration of the device has been changed.

The feature manager also contains a count of how many times the modules below it have updated their output registers. Each individual manager has a count of how many times the modules below it have updated their output registers and each individual module has a count as well. Therefore, if a master device executes the method Read Module Updates Counter and finds that none of the modules under a certain manager have updated their output registers since the last time the master read the values in the registers, the master does not need to waste communications bandwidth reading the same values again.

Methods and Modules are preferably assigned a security level. This permits the system to be configured such that certain users have access to all of the system functions while other users have access to only selected functions.

The Read Security Level, Read All Security Levels and Read Module Security methods can be used to determine what level of authorization is necessary to access the various methods and modules in the system.

The foregoing description of the preferred embodiments of the present invention has been presented for purposes of illustration and description. The described embodiments are not intended to be exhaustive or to limit the invention to the precise forms disclosed. Obviously many modifications and variations are possible in light of the above teachings. The embodiments which were described were chosen in order to best explain the principles of the invention and its practical applications. It is intended that the scope of the invention be defined by the following claims, including all equivalents. 

We claim:
 1. An intelligent electronic device for determining a desired power parameter, the device comprising:at least one detector which receives an electrical signal and generates a digital signal representing the electrical signal; a processor; object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects; and at least one of the modules comprising a power meter object module operatively connected to receive the digital signal as input data and generate at least one power parameter therefrom.
 2. The intelligent electronic device of claim 1 wherein the object logic further comprises a plurality of registers defining server objects which respond to method invocations from the modules.
 3. The intelligent electronic device of claim 2 wherein the registers are linked to the respective modules and wherein at least one of the links between one of the modules and one of the registers is programmable.
 4. The intelligent electronics device of claim 1 wherein the modules are configured such that a plurality of modules are arbitrarily linked to form arbitrary functional blocks.
 5. The intelligent electronics device of claim 1 wherein the object logic comprises an event log module and event log registers which record causes of events which occur in the IED.
 6. An intelligent electronic device for determining a desired power parameter, the device comprising:at least one detector which receives an electrical signal and generates a digital signal representing the sensed electrical signal; a processor; object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects; at least one of the modules comprising a power meter object module operatively connected to receive the digital signal as input data and generates at least one power parameter therefrom; and at least one of the modules comprising a manager module which organizes objects into a hierarchical structure.
 7. The intelligent electronic device of claim 6 wherein the manager module creates other modules.
 8. The intelligent electronic device of claim 6 wherein the object logic further comprises a plurality of registers defining server objects which respond to method invocations from the modules.
 9. The intelligent electronic device of claim 8 wherein the registers are linked to the modules and wherein at least one link between one of the modules and one of the registers is programmable.
 10. The intelligent electronic device of claim 7 wherein the manager module destroys modules.
 11. The intelligent electronic device of claim 6 wherein a method is invoked on the manager module to determine what modules exist in the hierarchy of the manager module.
 12. The intelligent electronic device of claim 11 wherein a method is invoked on the manager module to determine the addresses of the modules which exist in the hierarchy.
 13. The intelligent electronic device of claim 6 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been reconfigured, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been reconfigured.
 14. The intelligent electronic device of claim 9 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been updated, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been updated.
 15. The intelligent electronic device of claim 9 wherein the object logic comprises an event log module and associated event log registers which record causes of events which occur in the IED.
 16. The intelligent electronic device of claim 15 wherein the event log module and associated event log registers record times of events which occur in the IED.
 17. The intelligent electronics device of claim 15 wherein the event log module and associated event log register record effects of events.
 18. An intelligent electronic device for determining a desired measured parameter, the device comprising:at least one detector which receives an electrical signal and generates a digital signal representing the sensed electrical signal; a processor; object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects; and at least one of the modules comprising a module operatively connected to receive the digital signal as an input and generate measured parameters therefrom.
 19. The intelligent electronic device of claim 18 wherein the object logic further comprises a plurality of registers defining server objects which responds to method invocations from the modules.
 20. The intelligent electronic device of claim 19 wherein the registers are linked to respective modules and wherein at least one of the links between one of the modules and one of the registers is programmable.
 21. An intelligent electronic device for determining a desired measured parameter, the device comprising:at least one detector which receives an electrical signal and generates a digital signal representing the sensed electrical signal; a processor; object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects; at least one of the modules comprising a power meter object module operatively connected to receive the digital signal as an input and generate measured parameters therefrom; and at least one of the modules comprising a manager module which organizes objects into a hierarchical structure.
 22. The intelligent electronic device of claim 21 wherein the manager module creates other modules.
 23. The intelligent electronic device of claim 21 wherein the object logic further comprises a plurality of registers defining server objects which respond to method invocations from the modules.
 24. The intelligent electronic device of claim 23 wherein the registers are linked to respective modules and wherein at least one link between one of the modules and one of the registers is programmable.
 25. The intelligent electronic device of claim 22 wherein the manager module destroys modules.
 26. The intelligent electronic device of claim 21 wherein a method is invoked on the manager module to determine what modules exist in the hierarchy of the manager module.
 27. The intelligent electronic device of claim 26 wherein a method is invoked on the manager module to determine the addresses of the modules which exist in the hierarchy.
 28. The intelligent electronic device of claim 21 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been reconfigured, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been reconfigured.
 29. The intelligent electronic device of claim 23 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been updated, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been updated.
 30. The intelligent electronic device of claim 23 wherein the object logic comprises an event log module and associated event log registers which record causes of events which occur in the IED.
 31. The intelligent electronic device of claim 30 wherein the event log module and associated event log registers record times of events which occur in the IED.
 32. A monitoring system for monitoring a plurality of power parameters, the system comprising;a plurality of intelligent electronic devices (IED) each including at least one detector which receives an electrical signal and generates a digital signal representing the sensed electrical signal, a processor, object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects, wherein the modules are arbitrarily linked to form functional blocks comprised of networked objects, and at least one of the modules comprising a power meter object module operatively connected to receive the digital signal as input data and generate power parameters therefrom; a computer including a processor which invokes methods on other objects including the modules on the IEDs; and a communication network connecting the plurality of IEDs to the computer, wherein the computer configures the modules on the IEDs via the communications network.
 33. The monitoring system of claim 32 wherein the object logic in each of the IEDs further comprises a plurality of registers defining server objects which respond to method invocations from the modules.
 34. The monitoring system of claim 33 wherein the registers are linked to respective modules and wherein the links between at least one of the modules and at least one of the registers is programmable.
 35. The monitoring system of claim 32 wherein the object logic in the IEDs comprises a manager module which organizes objects into a hierarchical structure.
 36. The intelligent electronic device of claim 35 wherein the manager module creates other modules.
 37. The intelligent electronic device of claim 36 wherein the manager module destroys modules.
 38. The intelligent electronic device of claim 35 wherein a method is invoked on the manager module to determine what modules exist in the hierarchy of the manager module.
 39. The intelligent electronic device of claim 38 wherein a method is invoked on the manager module to determine the addresses of the modules which exist in the hierarchy.
 40. The intelligent electronic device of claim 35 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been reconfigured, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been reconfigured.
 41. The intelligent electronic device of claims 33 or 35 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been updated, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been updated.
 42. A monitoring system for monitoring a plurality of parameters, the system comprising;a plurality of intelligent electronic devices (IEDs) each including at least one detector which receives an electrical signal and generates a digital signal representing the sensed electrical signal, a processor, object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects, wherein the modules are arbitrarily linked to form functional blocks comprised of networked objects, and at least one of the modules comprising a power meter object module operatively connected to receive the digital signal as input data and generate parameters therefrom; a computer including a processor which invokes methods on other objects including the modules on the IEDs; and a communication network connecting the plurality of IED's to the computer, wherein the computer configures the modules on the IEDs via the communications network.
 43. The monitoring system of claim 42 wherein the object logic in each of the IEDs further comprises a plurality of registers defining server objects which respond to method invocations from the modules.
 44. The monitoring system of claim 43 wherein the registers are linked to modules and wherein the links between at least one of the modules and at least one of the registers is programmable.
 45. The monitoring system of claim 42 wherein the object logic in the IED's comprises a manager module which organizes objects into a hierarchical structure.
 46. The intelligent electronic device of claim 45 wherein the manager module creates other modules.
 47. The intelligent electronic device of claim 46 wherein the manager module destroys modules.
 48. The intelligent electronic device of claim 45 wherein a method is invoked on the manager module to determine what modules exist in the hierarchy of the manager module.
 49. The intelligent electronic device of claim 48 wherein a method is invoked on the manager module to determine the addresses of the modules which exist in the hierarchy.
 50. The intelligent electronic device of claim 45 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been reconfigured, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been reconfigured.
 51. The intelligent electronic device of claims 43 or 45 wherein the object logic comprises logic to determine if any module in the manager's hierarchy has been updated, and wherein a method is invoked on the manager module to determine if any module in the manager's hierarchy has been updated.
 52. A monitoring system for monitoring a plurality of parameters, the system comprising;a plurality of intelligent electronic devices (IEDs), each including at least one detector which receives an electrical signal and generates a digital signal representing the sensed electrical signal, a processor, object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects, and at least one of the modules comprising a power meter object module operatively connected to receive the digital signal as input data and generate power parameters therefrom; a computer including a processor and object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects including the modules on the IEDs, the computer object logic defining a virtual intelligent electronic device; and a communication network connecting the plurality of IEDs to the computer.
 53. A monitoring system for monitoring a plurality of parameters, the system comprising;a plurality of intelligent electronic devices (IED), each including at least one detector which receives an electrical signal and generates a signal representing the sensed electrical signal, a processor, object logic operatively connected to be executed by the processor, the object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects, and at least one of the modules comprising a module operatively connected to receive the digital signal as input data and generate parameters therefrom; a computer including a processor and object logic comprising a plurality of independent modules, each module defined by an active object which receives input data and generates output data according to a predefined function and which invokes methods on other objects including the modules on the IEDs, the object logic defining a virtual intelligent electronic device; and a communication network connecting the plurality of IEDs to the central computer.
 54. A process of operating a digital device comprising the steps of:providing a processor; defining object logic executable by the processor, including the steps of creating a plurality of independent modules, each module defined by an active object which receives a message and executes a predefined method and which invokes methods on other objects; managing the modules with a manager module, including the steps of organizing a plurality of objects into a hierarchical structure and providing access to all objects below the manager in the hierarchy; and linking the modules, in an arbitrary fashion, to form arbitrary functional blocks.
 55. The process of claim 54 further comprising the step of organizing the manager modules into a hierarchical structure from which the entire configuration of the digital device is ascertained. 